The iSMA-B-MAC36NL is a compact Master Application Controller with built-in different types of I/O and operating in Niagara Framework environment. Using the specific local I/O set 16x UI, 8x AO, 4xDI and 8x DO allows to use the device in different applications. The controller provides control, data logging, alarming, scheduling, integration and visualisation.
To allow IP connectivity there are 2x Fast Ethernet ports which can operate as two independent ports. Built-in 1x RS485 can be used to expand number of I/O by connecting MINI or MIX series I/O modules or to integrate with other subsystems.
iSMA-B-MAC36NL provides rich graphical interface displaying on a standard Web browser or on external display connected to built-in HDMI and USB port (touch-screen support).
There is another hardware version of the controller with the second RS485 port available.
- BACnet MSTP, Data Recovery Service, Web Service Ports fix and HDMI function are now available for N4.6 and 4.7.
16x Universal Inputs (16UI)
All Universal Inputs have 16-bit ADC which support the following types of inputs:
Temperature input supports the following types of sensors:
10K3A1, 10K4A1, Carel 10K, 20K6A1, 2.2K3A1, 3K3A1, 30K6A1, SIE1, TAC1, SAT1, Pt1000, Ni1000
For sensors Pt1000 and Ni1000 use only 16-bit resolution!
- Voltage input 0-10 V DC: input resistance 100 kΩ accuracy ±0,1%, measurement resolution 3 mV @ 12-bit
and 1 mV @ 16-bit
- Current input 0-20 mA (external resistor 499 Ω required)
- Resistive input 0-1000 kΩ: measurement resolution
for 20 kΩ load: 20 Ω @ 12-bit and 1 Ω @ 16-bit
- Dry contact input
- Dry contact inputs
- Fast pulse counter up to 100 Hz saved in SD Card
All Analog Outputs are equipped with 12-bit ADC provides 10 mV resolution and accuracy less than ±0,5%. They support the following output types:
- Voltage: 0-10 V DC max. load up to 20 mA
- PWM: 0,01 Hz, 0,1 Hz, 1 Hz, 10 Hz, 100 Hz
- Relay output (NO): max. 3 A @ 30 V DC
- Multicore Cortex-A Series ARM Processor
- 1GB DDR3 SDRAM
- Removable micro-SD card – 4 GB
(2 GB system reserved / 2 GB user storage)
- RS485 half-duplex, opto-isolated
- Baud rate from 2400 to 115200
- 2x Fast Ethernet (independent)
- 2x USB (1x OTG, 1x Host)
- HDMI type A (standard)
- Micro SD card slot
- Modbus RTU/ASCII/IP, BACnet MSTP/IP, oBIX, SNMP,
- Second RS485 (option)
- 24 V AC/DC
- Dimensions: 160x110x62 mm.
- Construction: UL approved,
self-extinguishing plastic (PC/ABS)
- DIN rail mounting DIN (DIN EN 50022 norm)
- Cooling: internal air circulation
- Operating temperature: -10°C to 50°C
- Storage temperature: -40°C to 85°C
- Relative humidity: 5% to 95%, no condensation
- Ingress Protection Rating: IP40 – for indoor installation
For any help please contact our support here
What is the default IP of the device?The default IP is : 192.168.1.123.
What Niagara version is needed to connect to this controller?At the moment the default Niagara version is N4.4 (184.108.40.206).
What should I do if I need to use Niagara 220.127.116.11?To install dist you can either copy the DIST FILES to your
%HOMEPATH%\Niagara4.4\sw\inbox folder and use commisioning wizard, or use Platform→Distribution File Installer, choose file and install.
What should I do if I need to use Niagara 4.6 and 4.7?
Please download the 4.6 and 4.7 update files HERE, into the zipfile you will find a file named “iSMA_MAC36_files_installer_v1.0.983”, this will copy for you all the DIST files into the relevant folders.After this procedure you will need to restart the Workplace and commission your MAC36NL with the 4.6 or 4.7 version.
What are the improvements for the MAC36NL with Niagara 4.6 and 4.7?
With the release of N4.6 and N4.7 for the MAC36NL you some new features:- BACnet MSTP - HDMI
- Data Recovery Service - Web Service Port Fix
Please see read the Release Notes.
What are the default platform Credentials?The default credentials are the same as to the Tridium controllers:
What communication networks are available?In this stage the Networks that work are:
- Modbus RS485
- Modbus TCP
- BACnet TCP
- BACnet MSTP available for version N4.6 and N4.7.
- Mbus TCP
- Niagara Network
What features are implemented into this controller compared to the Tridium Jace?The iSMA has the same features as a Tridium N4 controller:
-PX pages (web User Interface pages) HTML 5 web viewing
-Communication with Niagara controllers and Supervisors through Niagara Network
When commissioning I see this message: there is no Core software found that can be installed, what should I do?The core software is installed from the factoryfor version 4.4.73, you just need to press Next.
After using the commissioning wizard to install the Station and modules, I can see into the Application Directory that there are errors regarding the Web Server and I cannot access the controller from the webpage. How do I resolve that error and access the controller through the web page?At this stage the Web server works with the TCP port above 1024, so you will need to go and change the HTTP and HTTPs ports to be above 1024 (ex: HTTP port - 8080, HTTPs port 8443). After setting this up please restart the station. This issue was resolved in N4.6 and N4.7 release.
How does the Local IOs work?The Local IO driver it is still at an early stage and you will need to Download the Jar file. Put it into the Modules folder and restart the Workbench. Go and find the iSMA IO into the Palette. Into the Drivers add from the iSMA_IO Palette the iSMA IO Network, after that open the Property Sheet of the Drivers to see the recently added Network. Under it add the Local IO Device and under that add the points from the palette.
How do I change the Universal Input type?Open the property sheet of the UI and you will see the Input type property, by default it is set to Voltage.
How do I change the Analog Output type?Open the property sheet of the AO and you will see the Output type property, by default it is set to Voltage.
How can I use the HDMI function?After you have commissioned the controller on your N4.6 or N4.7 and install the iSMA_HDMI jar file, copy the HDMI service from the iSMA_HDMI pallette to the Service folder and you will need to go to the WEB service and activate the HTTP port and disable HTTPS Only. After you make those settings please reboot the controller.
What Shipping Methods are Available?We do UK next day delivery and 2 working days for Ireland We do Europe standard 3 day delivery. We do Worldwide delivery between 2 and 7 days depending on each country.
How Can I Return A Faulty Product?Returns are free of charge we will organize the pickup only in the case the product is faulty. Please contact firstname.lastname@example.org to obtain an RMA number first.
How Do I Track My Order?Once we ship your order, you will receive a tracking number and you will also find it in My Account section.
How can I place an Order?
You can place an order online and pay by credit/debit card if you do not have a Trading Account.
You can please your order online and pay by Trading Account if you have a Business Trading Account.
To open a Business Trading Account please fill in this form and send it back to email@example.com