How many inputs can I use?
4x Special Input - voltage, resistance, dry contact
4x Digital Input – dry contact
How many outputs can I use?
3x Digital Output 6 A (Fan Speed)
1x Digital Output 10 A (electric heater)
1x Digital Output 6 A (cooling actuator)
2x Triac 0,5 A @ 230 V AC or 0,5 A/0,3 A* @ 24 V AC (heating and cooling, actuators)
3x Analog Outputs 0-10 V DC (heating, cooling actuators and Fan Speed)
What protocols can I use?
How flexible is this?
Support 2-pipe or 4-pipe system, Preloaded universal applications, Adjust application by dedicated DIP-switch or freely program using Sedona Framework 1.2 Changing of the application is possible in real-time by USB port or over the network using simulator on PC in offline mode.
Leave a comment